UPS with a power of more than 3 kVA is connected to the mains and load through terminal block and should only be performed by authorized service center specialists. UPS malfunctions arising from self-connection not covered by warranty.
After completing connection of UPS by an authorized service technician, an act of completion drawn up, which must presented later when applying for warranty service. If there is an act of performance of work from an authorized service center, the warranty period for UPS excluding rechargeable batteries may counted from the date of completion of work on connection.
General recommendations for placement and connection of UPS:
Room intended for UPS installation must comply with following requirements:
UPS delivery to the installation site should be in the factory packaging. Do not disassemble the UPS, drop it or place it on side.
Attention! Independent opening of sealed parts and parts of UPS leads to a refusal of warranty service.
To reduce commissioning time, increase installation culture and simplify further equipment maintenance in preparation for installation, you must:
Compliance with above requirements will not only reduce labor costs when putting UPS into operation, but also reduce ownership cost of equipment.
Service phone: +7 (495) 518-92-82
Service email: firstname.lastname@example.org
Official website of the company: © Parus Electro, 2011-2020
All information published on the website is for guidance only and under no circumstances is a public offer determined by the provisions of Article 437.